Reliable advanced technology backed by experience, in response to today's needs
Small to medium size steam turbines from the SHI Group have a superior performance that has gained high credibility and is used as steam turbines in gas turbine combined cycles, as well as electric power generating facilities that use biomass or waste materials. Past performances for condenser type (multi-stage C type, and multi-stage axial exhaust type) steam turbines total about 6,500 units in about 80 countries around the world.
The axial exhaust type is an evolution of the condenser type steam turbine. Conventional condenser steam turbines generally expel the exhaust gas in an upward or downward direction, which is at a right angle to the axis. Changing this so that the exhaust gas flows in the direction of the axis resulted in a reduction in exhaust gas losses, and a significant improvement in energy efficiency became possible. In terms of layout, conventional types required a large space in the downward or upward, but the axial exhaust type turbines from the SHI Group direct the exhaust gas in the direction of the axis. Since a condenser is connected directly, the layout is simple and construction costs are dramatically reduced, while significantly contributing to a reduction in both time and cost in maintenance and inspections.
In the case of steam extracted at an intermediate stage of the turbine and supplied to the manufacturing plant, control of the internal extraction pressure makes it possible to supply gas in a stable manner, from low to rated load on the turbine. The internal extraction pressure control is a method used to maintain the gas extraction pressure at a certain level by controlling the pressure on the upstream side, using a pressure control valve, which is installed inside the casing of the turbine. Since an internal control valve can be installed in up to two stages (intermediate and low pressure steam), it is possible to supply gas extracted from a single turbine unit to two locations in the manufacturing plant.
|Type C Condensing Multistage Steam Turbine||Highly efficient, high output type multiple stage turbine|
|Condensing Multistage Axial Exhaust Steam Turbine||An evolved condenser steam turbine system with easy layout|
|Internal Extraction Pressure Control Steam Turbine||Reuses heat energy of steam extracted from the turbine|
|Type B Multistage Back-Pressure Steam Turbines||Necessary components have been standardized for easier maintenance|
|Stage Back-Pressure Steam Turbines
|Single-stage horizontal installation type compact all-purpose turbine, which is a representative product of the SHI Group|